- Green — Repeater up. All equipment and services are functioning. Last serviced March 14, 2018.
- Repeater Maintenance History
- The 2m TX antenna and one link beam need minor repositioning. The tower team is planning to reposition and tighten the antennas by the end of March 2018.
- Our Internet-controlled power switch is suspected of causing occasional controller resets during high temperatures in the repeater shelter. On 3/14/2018 we moved equipment that was blocking the cooling vents on top of the power switch. We are confident this was the cause of the thermal issue. We tested with a heat gun. We decided not to deploy the replacement power switch, but it is programmed and ready for future deployment.